Temperature 1-wire, (THS), 2m
A temperature sensor -55C ... +125C with a 1-wire interface. A cable length is 2 m.
A temperature sensor is connected to NetPing devices, that support a 1-wire interface. Temperature sensors are plugged with the help of RJ12 sockets, on which all 6 contacts are used. Electrically, all 1-wire sensors are connected in parallel to each other, therefore it does not matter to which 1-wire socket on a body of a device a sensor is connected.
To increase a length of a sensor cable, there is a need to use specific 1-wire cable extenders. A 1-wire splitter is included into a cable extender kit. It allows to branch a sensor network anywhere. An overall cable length of a 1-wire network must not exceed 70m. If necessary, it is possible to extend sensor flat cables without assistance, using a 6-wire cable, at least AWG24. There is a need to use special equipment for crimping RJ12 sockets. Use a 1-wire splitter to connect a sensor.
1-wire sensors have unique internal numbers, which allow a device to identify each sensor. When connecting a new 1-wire sensor to a device, there is a need to complete a procedure of a device reading an internal number. See more detailed information about a sensor plugin in a document "Firmware Description" for the device, to which you connect a sensor.
1-wire sensors plugin to a NetPing 8/PWR-220 v3/SMS device:
Connecting several 1-wire sensors to a NetPing 8/PWR-220 v3/SMS device with the help of a 1-wire splitter on 5 ports:
|Device dimenstions||25 x 7 x 7|
|Sensor cord length||2 m.|
|Thermal range||-55C .. 125C|
|Water proof case||Yes|
|Device suit||Sensor, zip package|
Cable extender 1-wire, 5m
Cable extender 1-wire, 10m
Cable extender 1-wire, 2m
UniPing server solution v3/SMS
NetPing 8/PWR-220 v3/SMS
UniPing server solution v3