NetPing Supply Voltage Sensor 995S2
- 21.00 USD
A sensor allows detecting the power voltage in the power outlet.
- it is manufactured in the case of the power unit with the IEC320 C7 (IP20) socket. It can be plugged into any outlet using a detachable power cord.
- has the internal nodes powered from the grid and thus may maintain operation in the range between AC 70...250 V with the frequency of 50/60 Hz.
- Triggering threshold: 178–193 V.
- Releasing threshold: 155–175 V.
- The output type is «dry contact» / normally closed and normally opened contacts (built-in relay).
- Loop is 1,5 meter long.
A sensor allows determining only the presence or absence of the voltage in the power outlet. A sensor does not determine the value of the voltage in the power outlet!
The output of the sensor is normally closed and normally opened relay contacts («dry contact», three wires: a normally closed wire — a common wire — a normally opened wire). When the voltage is below 65–78 V, relay contacts are opened. When the voltage exceeds 80–93 V, the state of the contacts is changed to the opposite.
A sensor is connected to the contacts IO and GND of the NetPing/UniPing devices depending on which logic level is needed when there is no voltage. The connection polarity of the wires from the sensors is irrelevant.
The information about connecting a sensor is indicated in the document named «User Guide» that is specific for every device that is connected to the sensor. The configuration information about a sensor and its functionality is specified in the document named «Firmware Description» that is specific for every device that is connected to the sensor.
If there is a need to determine if there is the voltage in a 3-phase circuit, ensure there are three power outlets, one for each phase, and use three power sensors.
A sensor is shipped with an inseparable cord with the tips at the ends. A length of a cord can be increased using loop extenders for the sensor RC-4 that are plugged one into another or independently using any wire with a cross-section of no less than 0,4 square millimeters. Ideally, a maximum allowed loop length is 100 meters.
|State of contacts||NO and NC|
|Device suit||NetPing Supply Voltage Sensor 995S2 — 1 pc.; quick start guide — 1 pc.; power cord IEC320 C7 to CEE7 XVII (SL-5+SL-8), 1,8 meter — 1 pc.; packing box + name sticker — 1 pc.|
|Device dimensions||80 x 45 x25|
|Operating temperature range||-30°C ... +50°C|
|Water proof case||No|
|Sensor cord length||1.5 meters|
|The unit case||Plastic|
|Technical documentation NetPing Supply Voltage Sensor 995S2||Go to|